What is an Arrangement 7 Fan?
Fan arrangements define the way a motor drives the fan, and how the motor mounts to the fan, based on AMCA standards. The Arrangement 7 Fan offers a maintenance-friendly and reliable design for fans with larger impellers, as the impeller is center-hung between two bearings. The entire fan assembly is assembled on a common base and can be either belt or direct drive.
Components of an Arrangement 7 Fan
The Arrangement 7 Fan includes a center-hung impeller with one bearing on the inlet side of the fan and the other on the drive side. An integral inlet box is required to protect the inlet bearing from the air moving through the fan. Both the housing and the integral inlet box are horizontally split for easier access and removal of the impeller. These fan components along with the motor are mounted on a common unitary base and provides one complete assembly for installation.
Other Fan Arrangements
- Belt Driven: Arrangements 1 and 9
- Direct Driven: Arrangement 4 and 4V
- Belt Driven OR Direct Driven: Arrangements 3, 8 and Plug
For an overview of all Fan Arrangements, visit Centrifugal Fans & Blowers and click on Arrangements
Hear it from the Application Engineer
Senior Application Engineer Chet White provides an overview demo in this 1-minute video.
When you’re ready to start your project, reach out and connect with one of our application engineers to discuss the details of your specification.
Related Content: More on Fan Arrangements
To see the fans referenced above, take a look at these additional videos:
- Industrial Fans: Belt Drive or Direct Drive
- Arrangement 4 Direct Driven Fans
- Arrangement 4V Top Mounted Fans
- Arrangement 1 Belt Drive Fans
- Arrangement 9 Belt Drive Fans
We welcome comments and questions via our LinkedIn Page, and you can always Contact Us or Request a Quote for more details.